DK8-BX10 Early Streamer Emission(ESE) Lightning Rod is designed according to IEC Standard High Voltage Testing Technology First Part: General Definition and Testing Requirement and GB 50057-2010 Design Specification of Building Lightning Protection. This lightning rod contains two parts: air termination(0.6 meter) and support accessory(1.2 meter), which can be combined into a integral through bolt. The Advance Time is 60μs. Under the same installation height, the radius of protection is larger then the ordinary lightning rod. With the advantages of light-weight and low load, it adopted stainless steel material, and can be install under hostile environment.
a. Accurate thunderbolt point.
b. Maintenance-free, do not need connect additional power.
c. Activate itself only when the thunderbolt forming, completely early discharge initially.
Item No。/Technical Parameter
|Discharge Current Capacity||200kA (10/350μs)|
|Amplitude Attenuation Rate||≥70%|
|Brupt Slope Damping Ratio||≥48%|
|Limiting Current Resistance Value||≤3Ω|
|Height||1.8m(0.6m + 1.2m)|
|Down Conductor||one or several round steel or the same sectional area steel flat.|
Suitable for direct Lightning Protection of mobile communication base station, satellite station, warehouse, meteorological observatory, petrol station, airport station, military radar station, etc.